BC Hydro, Canada
Air Cooled Hydro Generator, 457 MVA, 16 kV, 30 year old
Four Iris Power PDA Epoxy Mica Couplers (EMC) per phase
High Partial Discharge Levels Detected
Partial discharge (PD) measurements and data analysis have been performed on BC Hydro generators for approximately over 2 decades in order to identify stator winding insulation problems through analysis of the partial discharge signal characteristics.
The partial discharge patterns of this particular generator winding followed typical patterns with no polarity predominance between the positive and negative PD pulses. Also, a linear decrease in pulse density with increase in pulse magnitude was shown. In the PPA plot, the PD clouds were triangular shaped and centred at 0° and 180° in the negative and positive cycles, respectively. The Qm was about 500 mV.
Figure 1: Partial Discharge Results
Visual Inspection Confirms Severe Partial Discharge at the Stress Control Grading Paint Area
A 457 MVA, 16kV generator was subjected to severe discharge in the grading paint area which caused grading paint damage and the build up of white power on the top and bottom ends of the stator winding bars.
Figure 2: Stress Control Grading Paint Damage due to Partial Discharge
Excerpts from paper “Partial Discharge Measurements on Hydro Generator Stator Windings Case Studies”, by S. Li and M. Chow” in IRMC June 2006